Your most assured of clean room engineering services
In addition to the high requirements for cleanliness, t […]
In addition to the high requirements for cleanliness, the clean operating room should be safer for the fire resistance of the material, and must be protected against life. Fire prevention advice for clean operating rooms
1. The clean surgical department should be located in a building with a fire rating of not less than two.
2. The cleansing department should be divided into separate fire compartments. When it is in the same fire zone as other parts, effective fire and smoke separation measures shall be taken, and partition walls with a fire resistance of not less than 2.00h shall be used to separate from other parts; doors connected to non-clean surgical parts shall be Use fire doors with fire resistance not lower than Class B (except for direct access to open exterior corridors or direct external doors), or other appropriate fire prevention technical measures.
3. The technical interlayer of the clean surgical department should be fireproof and smokeproof in connection with the operating room and auxiliary room. The fire resistance of the partition should not be lower than 1.00h.